Matt Zimmerman: Do you have an image of the thimble being placed? You cut that out of the
video. I am wondering if you just dropped it in through the
siding/wrap/wall with no flashing whatsoever. That is a huge water leak
waiting to happen.
Chris Schinning: It looks like the interior flue pipe is upside down (female flange on top)
Mathieu Khoury: HI, I have the exact same installation and i get cold air coming in and
some water drops. I suspect ice and/or condensation is forming between the
dual walls of the outside chimney. Is it possible? Will scealling the
joints of the chimney with caulking do the job? Thanks for relying. Cheers!
Brian Perendy: just the wall studs for the weight. wow.
dennis bailey: Two feet to go???at bottom of eaves....suppose to be three feet above the
ridge on a level plane to avoid down draft....
E Cole: This guy is going to burn this house DOWN! He has chimney touching a
combustibles!!! You need a wall thimble for your pass through. This hearth
doesnt meet code! Your clearance to combustibles are way off. The #'s he
states are even wrong. You need those bands every 8ft not 10, clearance is
2in, not one.
dennis bailey: from the ridge of the house..... chimney should be 3 feet
above.......draw a horizontal line from the ridge and top of chimney should
be 3 feet above that point....maybe it's diff today but that's how it used
Alan Zelez: Thank you for posting. Really good video.
liam murphy: umm just one thing he has done wrong you can NOT use a horizontal peace of
pipe coming out of the rear any more than 6 inch because of the gases he
has 12-14 inch peace it will cause carbon monoxide its bad .
dirtTdude: how much did all that triple wall pipe cost? my budget for woodstove
installation in my workshop is only 40 dollars... its a pole building made
out of non combustible material...
DmeshOnPS3: estimated cost of supplies? besides the wood stove. also, how much was
the wood stove? lol. what would you charge for labor? i want to have
that done , oil is too expensive!
nzinga zindua: Can the wood burning stove be connected directly to the house chimney? And
if so, does the house chimney need to be lined? Thanks for posting.
Gorden Denluck: where did you buy the parts from?
nekrobillyhenry666: lookin good!
mrEnergy511: Save some money and reduce to 6" the parts are more available and cheeper!
I can sell you what you need and ship it to you. I have paypal they offer
some very nice buyer protection. call me 801-960-6484 mon- fri 9-5 Matt
GZRGXR: Hi Matt, I'm getting ready to install a Metalbestos 8T-Twk Thru-Wall
Support Kit (TWK) and the instructions for my kit shows the wall support
bracket with the triangles pointing down "like a shelf bracket would" in
your video you have the triangle pointing up, is that because you are using
a different kit?
mrEnergy511: Sorry dude you are wrong! Galvanized metal is for outdoor use!!! 2100
degree class 'A' chimney pipe is made to be exposed to the elements.
mrEnergy511: What you will want to do is build a "Heat Sheild Wall". To do this you will
need to have an air space between your Cumbustable wall and your Heat
Sheild Wall. Start with Metal Studs by screwing them to the Cumbustable
wall Verticaly with the flat side out. You will need some long screws! Next
just install cement board over the studs alowing for air flow 1" top and
bottom with studs vertical. This will give you 1 1/2" of air flow space
between the two walls. I need to make a video on Heat sheild!
mrEnergy511: If your installing a Chimney Pipe through a Brick Wall you will do the same
thing only use a grinder with a diamond blade. You could also use a
circular saw with a diamond blade or an abbrasive blade. Brick is
non-conbustable so there are no clearence issues. Are you planing to pipe
into an existing Chimney? Or is it just a brick wall?
Azim Ali: Great stufff***********
Bob Valdez: Thank you for that helpful info. I'm also ready to install a woodstove and
my question is it better to install woodstove pipe straight to the wall vs
up the stove then 90degree turn toward the wall. Concern about the
effectiveness of the draft
Mike T: I want to install the same type of wood stove but in my basement. Rather
than shoot up through two floors and a roof...I am thinking about shooting
to outside through the basement wall then straight up the side of the
house. As in this video, I will run into the roof eve. Can I elbow around
it? As long as I use good bracing?
JTB1956: You'd do best to stay with the smoke outlet size of 7" , or upsize it to
8". There isn't much 7" chimney around anymore..but I installed a good bit
of it back in the '80's and early '90's. It may be tempting to downsize it
to 6" for cost and availablity, but doing so is a No-No unless your stove
installation instructions allow it. If you're still not sure of your
project get some help. It ain't brain surgery but there IS a learning curve.
mrEnergy511: Good stuff! That will work
mrEnergy511: Thanks for watching my video and for your kind words! I install Wood Stoves
and Fireplaces every day.
Tim Richardson: I love your videos! You always explain everthing in detail, that is much
appreciated! I have a question, I am lookinng to install an All nighter
wood stove, with the 6 inch rear flue, do I have to buiild a wall
''hearth'', or just a floor hearth? The stove says it needs to be away 36
inches from any combustables, but I can't have the stove sticking out into
the middle of the room, what materials would you suggest that I use for the
wall behind the stove? Thank you very much!
mrEnergy511: Cool Man! Thanks for the comment. You may be able to find a Wood Stove used
for a few hundred bucks and save a lot of work and money! Unless you have
the time and some materials lying around to build it. Then I would have to
say go for it!
mrEnergy511: 20 years installing wood stoves and fireplaces! I'm sorry to let you know
you were misinformed. You look like an artist and I am a contractor who is
lisensed to install Class 'A' chimney pipe. Why do you think they GALVANIZE
chain link fence. To hold up to the weather! I think you should stick to
what you know like playing that ther gitar! Next time you get FREE advice
ask more than one person! I have layed a lot of pipe my friend and I'm sure
you have done a lot of stroking of your instrument!
bgoodd: Do you have a video of installing one through brick?
ozan gurkan zeytun: I wonder smthg about the support.How can ıt carry the vertical load on it.
what about the thickness of the support plate ?
woody1977321: I know this material is marketed for this purpose but that's some weak ass
stuff - I prefer heavy duty - like some good schedule 40 metal pipe!
Karen Harvey: the hole that goes through the wall does it have to be bigger or would the
pipe fit snug in hole. We got the dural vent triple through the wall kit
and on the inside black stove pipe
mrjrtolkien: Can you please give a rough estimate of the cost for the piping etc?
mrEnergy511: elbow around the eve... $200 for a pair of elbows is a good amount of money
to spend if you don't need to!
mrEnergy511: You must have proper clearance from your pipe to a combustable wall. 12 to
18 inches for single wall black stove pipe. 6" for dbl wall
mrEnergy511: NO WAY! 7" is old school!!! most all EPA wood stoves are 6" and thats is
the way to go. 20 years of installing and when I started 7" was going out.
2013 bro get rid of your mullet! 6" is all you need for a wood stove with a
6 inch collar...
Aj A.: Thanks for the good info. I have a question regarding the max elbows you
can use with a pipe, also can i run some of the pipe in 45 degrees angle?
Luigi Rizzo: What is your opinion of the Duraplus triple wall system they sell at Home
Depot? Any good for a Morso 6148 wood stove.
jjs777fzr: I believe you are incorrect - sounds like you stated you 'could' use elbows
on the exterior. As fingers967 stated - the install manual states it is not
approved for exterior applications. Since the building inspector/fire
inspection relies in part on the install guide of the product you used and
NFPA211 - it would simply not pass inspection. I'm not saying I wouldnt do
it...but it is technically against the manufacturer install manual and
therefore not acceptable during a diligent inspection.
Matthew LaRusso: Wondering where you purchase your Metal-Fab parts from. I am installing an
Elmira stove that has 7 inch chimney top port. I have a 7 inch ID metal fab
type A T and a few pieces of type A pipe. Looking for the wall thimble ,
short wall pipe, and a few long pipes for outside. I seen some on Amazon
and went to the metal-fab website. Very confusing... Also looking for the
wall mount triangle support and wall supports... any help would be
appreciated... Thanks Matthew...
frankthetank481: very informative video. I've been toying with the idea of building a wood
stove for my garag/shop. I'm glad I watched this video.
JTB1956: Yeah...but didn't that fellow write that the "top port" of his stove is
seven inch? I don't downsize a chimney unless the stove mfr. says it's OK.
(and I wouldn't do it then anyway).
cadmanwells: According to UK Building Regs this installation wouldn't comply as any
horizontal length of flue has to be no longer than the internal diameter of
the flue ie/ 6 inches. So if you happen to be looking at this in Great
Britain your flue pipe exits through the wall at 45 degrees into a 135
degree tee piece on the outside of the wall.Also the heatproof area of wall
behind the wall varies according to the type of stove but usually requires
70mm of non combustible material.
Gary Bottger: If you have a porch roof on the front of your house, can you vent it out
that way or does it need to be ran all the way up to the main roof? Using 2
45% angles I can get 10 foot out from the main house going up through the
mrEnergy511: Yes you can! A pair of elbows will cost you about $200. A roof flashing
will cost $30 or $40.
woody1977321: That wire is way to close to your heat source!
Wood Stove through wall Chimney Pipe Installation Howto4.8
out of 5
Omega Red: very nice video m8!!!!!!!!!!! Abigail Fano: And your brother is annoying af vjmamens: awesome very nice TIDG3YxMcDON4LD: the last gun you unlock is the AS VAL at rank 45 superlizerd1: EVERYTHING χχgιαиα яσχXx: Can someone plz help with my situation plz well my cousin came over and he was playing on my 3Ds and forgot to bring it inside and left it out in pouring rain and I got it to go on once but the battery drained and I can't get it back on again and not only that I see the charger light on but I think it might be alive but I'm not sure also my power button is a little loose and I'm not sure if that's why I can't turn it on or what. Does it need a new battery or anything plz help Colleen Shipp: I think that would be great, I run on a somewhat regular basis in the non-snow months, I really loved that 30/30 interval thing in your program. It would be cool to have some other running workouts. :)